Refrigerated light hydrocarbon fluids — General requirements for automatic level gauges — Part 2: Gauges in refrigerated-type shore tanks
ISO 18132:2008 establishes the general requirements for the specification, installation and calibration/verification testing of automatic level gauges (ALG) used for refrigerated light hydrocarbon fluids, i.e., LNG and LPG, stored in bulk storage tanks on shore at pressures close to atmosphere. ISO 18132:2008 is not applicable to pressurized shore tanks.
Hydrocarbures légers réfrigérés — Exigences générales pour jauges de niveau automatiques — Partie 2: Jauges pour réservoirs côtiers de type réfrigéré
Standards Content (sample)
Refrigerated light hydrocarbon fluids —
General requirements for automatic level
Gauges in refrigerated-type shore tanks
Hydrocarbures légers réfrigérés — Exigences générales pour jauges de
niveau automatiques —
Partie 2: Jauges pour réservoirs côtiers de type réfrigéré
---------------------- Page: 1 ----------------------
This PDF file may contain embedded typefaces. In accordance with Adobe's licensing policy, this file may be printed or viewed but
shall not be edited unless the typefaces which are embedded are licensed to and installed on the computer performing the editing. In
downloading this file, parties accept therein the responsibility of not infringing Adobe's licensing policy. The ISO Central Secretariataccepts no liability in this area.
Adobe is a trademark of Adobe Systems Incorporated.
Details of the software products used to create this PDF file can be found in the General Info relative to the file; the PDF-creation
parameters were optimized for printing. Every care has been taken to ensure that the file is suitable for use by ISO member bodies. In
the unlikely event that a problem relating to it is found, please inform the Central Secretariat at the address given below.COPYRIGHT PROTECTED DOCUMENT
© ISO 2008
All rights reserved. Unless otherwise specified, no part of this publication may be reproduced or utilized in any form or by any means,
electronic or mechanical, including photocopying and microfilm, without permission in writing from either ISO at the address below orISO's member body in the country of the requester.
ISO copyright office
Case postale 56 • CH-1211 Geneva 20
Tel. + 41 22 749 01 11
Fax + 41 22 749 09 47
Published in Switzerland
ii © ISO 2008 – All rights reserved
---------------------- Page: 2 ----------------------
ISO (the International Organization for Standardization) is a worldwide federation of national standards bodies
(ISO member bodies). The work of preparing International Standards is normally carried out through ISO
technical committees. Each member body interested in a subject for which a technical committee has been
established has the right to be represented on that committee. International organizations, governmental and
non-governmental, in liaison with ISO, also take part in the work. ISO collaborates closely with the
International Electrotechnical Commission (IEC) on all matters of electrotechnical standardization.
International Standards are drafted in accordance with the rules given in the ISO/IEC Directives, Part 2.
The main task of technical committees is to prepare International Standards. Draft International Standards
adopted by the technical committees are circulated to the member bodies for voting. Publication as an
International Standard requires approval by at least 75 % of the member bodies casting a vote.
Attention is drawn to the possibility that some of the elements of this document may be the subject of patent
rights. ISO shall not be held responsible for identifying any or all such patent rights.
ISO 18132-5 was prepared by Technical Committee ISO/TC 28, Petroleum products and lubricants,
Subcommittee SC 5, Measurement of refrigerated hydrocarbon and non-petroleum based liquefied gaseousfuels.
This part of ISO 18132 together with ISO 18132-1 cancels and replaces ISO 8309:1991, ISO 10574:1993 andISO 13689:2001, which have been technically revised.
ISO 18132 consists of the following parts, under the general title Refrigerated light hydrocarbon fluids —General requirements for automatic level gauges:
⎯ Part 1: Gauges onboard ships carrying liquefied gases
⎯ Part 2: Gauges in refrigerated-type shore tanks
© ISO 2008 – All rights reserved iii
---------------------- Page: 3 ----------------------
Large quantities of light hydrocarbon liquids consisting of compounds having primarily one to four carbon
atoms are stored and transported in bulk as refrigerated liquids at near-atmospheric pressure. These liquids
can be divided into two main groups: liquefied natural gas (LNG) and liquefied petroleum gas (LPG).
In general, the quantity of these light hydrocarbons transferred is determined and recorded on the basis of
volume and/or mass, with the energy content calculated in calorific units. If the static-measurement method is
used, the liquid level in the tank is one of the variables which most significantly influences the determination.
In addition to the level measurement, the following parameters are needed to determine the quantity andenergy content of the light hydrocarbons in a bulk storage tank:
a) tank calibration table;
b) composition of and/or physical data for the liquefied gases and vapour;
c) vapour pressure, vapour and liquid temperature;
d) volume of liquid in the pipelines;
e) status of the flush valves for connecting lines.
The various error factors that influence the quantification based on measurements of liquid level areconsidered in Annex A.
It is necessary to gauge shore tanks for one or more of the following reasons:
a) tank farm operations and process control;
b) tank inventory control;
c) where parties involved require custody transfer on shore tanks.
ISO 18132-2 removes technical dependency and ensures that the market is open to all newcomers in thisindustrial sector.
iv © ISO 2008 – All rights reserved
---------------------- Page: 4 ----------------------
INTERNATIONAL STANDARD ISO 18132-2:2008(E)
Refrigerated light hydrocarbon fluids — General requirements
for automatic level gauges —
Gauges in refrigerated-type shore tanks
This part of ISO 18132 establishes the general requirements for the specification, installation and
calibration/verification testing of automatic level gauges (ALG) used for refrigerated light hydrocarbon fluids,
i.e., LNG and LPG, stored in bulk storage tanks on shore at pressures close to atmosphere.This part of ISO 18132 is not applicable to pressurized shore tanks.
2 Normative references
The following referenced documents are indispensable for the application of this document. For dated
references, only the edition cited applies. For undated references, the latest edition of the referenceddocument (including any amendments) applies.
OIML R 85, Automatic level gauges for measuring the level of liquid in fixed storage tanks3 Terms and definitions
For the purposes of this document, the following terms and definitions apply.
automatic level gauge
level gauge that automatically measures the liquid level in a tank, either by innage or outage (ullage)NOTE An ALG is also commonly referred to as an automatic tank gauge (ATG).
tank lowest level that corresponds to zero level and zero volume in tank table
area in which an explosive gas atmosphere is present, or can be expected to be present, in quantities such as
to require special precautions for the construction, installation and use of apparatus[IEC 60079-10]
© ISO 2008 – All rights reserved 1
---------------------- Page: 5 ----------------------
upper reference point
point clearly defined on the gauge hatch directly above the datum level to indicate the position (and upperdatum) from which ullaging should be carried out
NOTE It is often the top of the mounting flange of an ullage ALG.
distance between the upper reference point and the datum level
distance between the liquid surface in a tank and the datum level
NOTE This is also known as innage.
distance between the liquid surface in a tank and the upper reference point
lower reference point
lowest measurable level located above the datum level that can be measured by an ALG3.9
total error including the intrinsic error of an ALG and error due to the effect of installation and operatingcondition
error of an ALG when tested under controlled condition as specified by the manufacturer4 Safety precautions
International Standards, government codes and regulations on safety and material compatibility precautions
applicable to light hydrocarbon fluids shall be followed when selecting and installing ALGs. In addition, specificrecommendations from ALG manufacturers should be followed.
4.2 Equipment precautions
4.2.1 All ALGs shall be designed and installed in accordance with applicable national standards and/orInternational Standards. See OIML R 85.
4.2.2 All ALGs shall be certified for use in the hazardous-area classification that corresponds to theirinstallation.
4.2.3 All ALGs should be maintained in safe operating condition. Manufacturers’ maintenance andoperating instructions specific to the ALG should be complied with.
5 Conformity to national standards and regulations
In addition to conformity with this International Standard, all ALGs shall also conform to OIML R 85.2 © ISO 2008 – All rights reserved
---------------------- Page: 6 ----------------------
6 Specification of level gauges
6.1 Compatibility with process conditions in the tank
All ALGs shall be designed to withstand cryogenic and corrosive conditions, turbulence in the fluid andvibration in the fluid and operating environment.
6.2 Provisions for routine maintenance
All ALGs shall allow routine maintenance to be performed without compromising the integrity of the tank. All
ALGs shall have provisions to allow field calibration or verification without taking the tank out of service. This
shall include means of verifying the level gauge accuracy at high and low levels.6.3 Self-diagnostics or other measures
All ALGs shall provide self-diagnostics or other means to minimize the time required for trouble shooting,searching for the cause(s) and eliminating the abnormal condition(s).
6.4 Countermeasures against sudden malfunctions
For ease of maintenance and of repair in case of a malfunction, ALGs should preferably be installed such thatthey can be isolated from the tanks, e.g. through an isolation valve.
6.5 Compatibility for electro-magnetic and other environmental conditions
All ALGs shall be designed for electromagnetic compatibility, complying with user requirements and otherproper standards, whic